|Item #5357 & 5358
Two (2) Used Langbein Engelbracht/TANN Regenerative Thermal Oxidizer (RTO).
5,000 scfm capacity. TANN Model TR595. TANN Serial # 1035-08.
Manufactured in 2008 and treated emissions at a solar cell plant.
Two-can design with random-pack ceramic media and
pneumatic valves. Used for less than one year. In excellent condition
internally and externally.
Unit includes the following:
Maximum design flow- 5,000 scfm @ up to TBD deg F process temp
95% effective heat exchanger (ceramic media in two chambers)
Pneumatic valves (horizontal) for flow direction changes through media
Main exhaust fan with 40 hp TEFC motor & Allen Bradley Powerflex
Variable frequency drive
Insulated poppet valves, fan and stack base
Allen Bradley 5/03 PLC with Allen Bradley Panelview+ 700 interface
Combustion blower with 3.0 hp TEFC motor and inlet silencer
Fresh air damper with pneumatic actuator
Isolation damper with pneumatic actuator
Eclipse Therm-jet burner
Exhaust stack (20 feet from grade, mild steel, 22” internal diameter)
Yokogawa 6-pen chart recorder with digital readout
Complete owner's manual with electrical and mechanical drawings.
Process isolation damper(s), fan balancing, painting, shipping, installation, permitting or other items or services not listed in this quote.
Weight: Approx. 40,000 lbs (including ceramic media)
Dimensions: Approx. 23’ long, 12’ wide, 17’ tall (excluding stack)
Electrical Requirements: 460/3/60 at 37 FLA
Gas requirements: 1,000 scfh max @ 5 psig (1” NPT inlet)
Compressed Air requirements: 20 cfh @ 80-100 psi; -40F dew point, .75” NPT
SUMMARY OF REFURBISHING:
If purchased refurbished, we will refer you to a qualified company to perform the following work and they will warranty 95% VOC destruction
for 90 days from start-up or until the first stack test, whichever comes sooner.
Flow Control Valve/Pneumatic System:
Test pneumatic valves and repair/replace as necessary
Leak test pneumatic supply lines, solenoids & air cylinders: repair as necessary
Gas Train/Burner System:
Test components in gas train and repair/replace as necessary
Test UV scanner, repair/replace as necessary
Clean or replace burner sightports
Test ignition transformers and spark igniters and replace as necessary
Bench test main motor and replace bearings as necessary
Bench test combustion blower motor and replace bearings as necessary
Bench test main fan shaft bearings and replace as necessary
Install new fan belts
Test all actuators, regulators, pressure switches, etc. and replace as necessary
Many other fixes that arise through the act of refurbishment